I know that this has been asked before, but how serious is it to have a neutral (grounded conductor) and a ground (grounding wire) share the same lug on a main distribution panel.
The panel in this photo shows two of of this very scenario. What exactly is the hazard? Can the neutrals share a lug?
Also, I couldn’t get any information of of the panel.