Quick question regarding service disconnects. I have tried to search for more info on the forum before posting.
I could not locate a service disconnect.
I little background, a standby generator (Cummins Onan) was installed in 2007, service drop goes directly from meter into the generator transfer panel, then to the “main” panel. It is over the 6 step rule, no other (sub)panels. Any help/advise would be greatly appreciated.