Originally Posted By: jmyers
This post was automatically imported from our archived forum.
Since this is a main lug panel, I would have to assume the Service Disconnect is upstream and present. It appears it may be a split buss to comply with the six disconnect, switch rule. If that is the case, there can be no more than six breakers or switches or any combination of, to turn off all the power to this property.
The neutrals and grounding wires need to be on separate bars, and the neutral needs to be floating (not bonded to the metal on the panel) if this is indeed an equipment panel (sub panel).
Neutral wires are only allowed one per termination, grounding wires would have to follow the manufacturers installation instructions as to how many of what size are allowed to be placed under each termination.
Hope that helps. ![icon_cool.gif](upload://oPnLkqdJc33Dyf2uA3TQwRkfhwd.gif)
A & N Inspections, Inc.