this Pushmatic has two 100 amp breakers labeled “main disconnect”
they are the top breakers in each of the two columns.
notice the way the 120 volt legs strap back and forth from the columns.
am i to assume this is actually a 200 amp service.
panel did not have a rating
entrance conductors were rated for 200 amp…CL200 meter.