Looking for some clarification on the Panel set up from today’s inspection please
- Service Panel has 100 amp OCP, but the Neutral bypasses the breaker and straight to Distribution
- Service Panel has disconnected Bonding Strap
- Distribution Panel has installed Bonding Strap
Question is, does the Neutral SE Conductor, by bypassing of the Service Disconnect in the exterior Main Service Panel now make the Distribution Panel the Service Disconnect?
And does the 100 amp breaker outside become just a “switch”
Or is this a Split Bus Panel?
Sorry if this sounds like a goofy or poorly worded question, I just confused myself by typing it!!!
Ps. I know about overheated SE Neutral at Dist. Panel, not sure if that matters in the context of primary
question though, but maybe it does??