Recommended that water logged panel be removed from “wet location” and new service run to “dry location” by a qualified, licensed electrician.
Well they moved it - living room dry location ok great, but sloppy work.
Checked the original location of the main panel and see it being used as a j box. :roll: propped by a 2x4 over a puddle, secured to the foundation … yea by a water logged/rotting piece of OSB. :shock:
my report states: "Old main panel used as a junction box for the new service. this is a safety hazard as the “junction box is located in a wet location.
This installation is not recognized as a safe installation per national standards. A Qualified, licensed electrician should be consulted to properly relocate/rewire main panel/junction box/s”
Tom I may have to give you my next re-inspection fee so you can keep me from possibly causing injury to this hack if he is present when I do go back to re-inspect this work for a second time!
Techincal term for this brain dead hack installation - unfreakinbelievable!
PS- he charged the current homeowner over $2,000.00 for this cluster****. :roll: