One 240 wire going to cabinet under range top to a junction box. Two wires coming out of junction box; one each to the electric range top, and the other going to wall oven. I called it out to be separate.
“The circuit for the oven and stove is code compliant. NEC table 220.19 note #4 says: the branch-circuit load for a counter-mounted unit and not more than two wall mounted ovens, all supplied from a single branch circuit and located in the same room, shall be computed by adding the nameplate rating of the individual appliances and treating this total as equivalent to one range”.