I did a pre-listing inspection yesterday house I expected many years ago and found these:
[size=2]There were two bay windows at the front of the house that had the same condition and the same cause.
The client had a repair done on moisture intrusion and felt that the situation had been corrected and no longer existed (other than a bleeding water stain through the ceiling paint).
Moisture meter: 90% Rh
Inadequate caulking around windows and brick veneer cracking was never addressed in the repair. Silicone was utilized to repair where the contractor believed the leak to be at the copper roof to brick veneer flashing.