2002 I believe is when this was done. This is a 200 amp main panel in a detached garage feeding a 200 amp panel in the house. The wires are tied directly into the hot bars at the bottom of the main panel with no breakers at all except the main disconnect at the top. I’ve never seen this type of hook up before. I know the licensed electricain that was labeled on panel. Although I do not know if he did this. Owner bought this place in '05 so she does not know either. Technically it does follow a disconnect but I’m not sure it is right or wrong this way. Help me out guys.