My house built in 2005 in South Florida. A/c unit is by Trane. The system is sweating a lot/ lots of condensation on the unit. The handler is in the garage. I have cleaned out the drain tube outside with the hose and flushed it out and opened the panel and added bleach water to the drip pan yesterday. The evap coil did look dirty, the filter is new. In the picture I circled where it is leaking water. That is the blower motor area, then in the middle the evap the to the far right the filter. Is the water normal? or any tips what I might need to do.