I have a question regarding the service entrance and I guess a lot of other unknowns,haha.
I’ve been inspecting for a little over a year and this is the first for me. The home is 100 years old and has a fuse box electrical panel along with a newer sub panel. I could not see the service meter because it was contained behind wall enclosure in the picture below and I am really not sure on the service amperage or anything going on here.
Can anyone help on how to advise my client on this situation?