Originally Posted By: psabados
This post was automatically imported from our archived forum.
The schedule 80 PVC was neatly cut at the inside of the footer. The conductors then ran on grade (gravel) over to the rear of dwelling.
[ Image: http://www.nachi.org/bbsystem/usrimages/more/IMG_4501.jpg.JPG ]
Also note that the conductors are in direct contact with one of the support posts.
[ Image: http://www.nachi.org/bbsystem/usrimages/more/IMG_4504.jpg.JPG ]
Over the exposed PVC water line, and the A/C line sets
Finally into the breaker box area from beneath
[ Image: http://www.nachi.org/bbsystem/usrimages/more/IMG_4506.jpg.JPG ]
Along with a few interior electrical conditions that were found this is being referred for additional evaluation by the licensed electrician. Sparky comments welcomed for repair recommendations