Originally Posted By: Dave King
This post was automatically imported from our archived forum.
Currently my elctrical set up is this..
100 amp service lines (I've contacted my electricity companyto confirm)
60 amp double fuse disconnect (throw switch)
200 amp breaker panel (new installation - previous owners)
My question, is it safe to remove the 60 amp disconnect, and re-wire from the meter directly to the panel? I would like to upgrade to the 100 amp service available to me. I seem to remember some issues with the panel being rated higher then the service entry.
Thanks in advance...