Originally Posted By: jpope
This post was automatically imported from our archived forum.
I am beginning to see these more and more lately. Should we be testing these?
Am I correct in assuming that if both hot and neutral of the same circuit are not connected to the breaker, the AFCI will not function properly?
Are these generally used only where the circuit wires may be penetrated by a nail or screw, or is there some other criteria used to determine where these are required?
JPI Home Inspection Service
"At JPI, we'll help you look better"