4 point for a 1949 home in jacksonville florida.
There is one circuit of multistrand aluminum wire with the hot and neutrals covered in cloth. Could not actually see if the insulation was cracked and therefore rubber or not.
Marked it as possibly cloth wiring, get confirmation from electrician.
Insurance agent just called me to ask me to remove that from the 4 point because an electrician said it is not cloth wiring. I asked her to send me that in writing. My email reply to her is in the images attached to this post.
Looks like he confirmed it was cloth wiring, what you think?
Additionally, do you check “improper grounding” if there are any old 2 wire, ungrounded circuits in the house?