Supposedly this was done by a licensed electrician and sign off by the City inspector. ( this was a flip) # 14-2 wire out of the main service panel through a weather head, tied into 2 awg AL triplex , only 8 feet off the ground running through the back yard then re-attached to #14-2 and run through a pipe into the garage. This cannot be right ! Right?
The #14-2 w / ground was typical interior rated NM (Romex) . Also, this # 14 wire was protected by a 20 amp breaker in the panel.
How would you word this in a report , besides just saying that it was FUBAR and recommending eval by a qualified electrical contractor?