We have a problem house built in 2008 in the country no AHJ inspection total electrical 5 ton heat pump with 4 15 KW strip heat, 2 electrical cook stoves remote cook top 2 whirlpool tubs a private well for water and Aerobic septic system 3 bathroom exhaust fans with electric heaters and one 50 gallon electrical water heater.
My write up was a little different than what was on the Realtor sheet.
The main panel was 200 amp and had a 100 amp sub feeding the additional panel side by side. As you can see I exceeded the 80% a bit.
I find this a lot but always on a home that has been added on to one or more times and the electrical was not updated. This was my first for a new home the electricians were so proud of their work they signed and dated the inside of the panel. 218 amps sure makes for nice thermal images