It seems like this is a problem I see often. There are no more breakers and when the air conditioer is installed it is double tapped improperly to the main breaker.
This panel was improper covered, pointed screw a broken breaker.
My question is on the air conditioner panel. I only see 2 wires and this is a 220 circuit. Besides the obvious double tap is this also improper wired for a 220?
I need to buy some panel screws. It seems like there are a lot of improper screws being inserted and instead of inserting these back in I should put in some proper ones. How much does a box or bag of deadfront blunt ended screws cost?