Good Evening Gentlemen
First time posting on this thread.
I did a 4 Point today and found a Cutler-Hammer breaker with a double-tap. The breaker is labeled a “1 Pole Unit”. I think I am correct in calling out this as a deficiency, however the last Inspector that did a 4 Point here (2005) labeled it as a legitimate breaker rated for two conductors, in other words…he passed it. Please advise if you have a moment
Thanks so much Matt