Is there anything wrong with this particular connection? This is a water heater in a small utility closet in the garage.
It’s wrong. An appliance connector is to connect the appliance to the gas piping. It isn’t to be used in lieu of gas piping. Here’s a great article.
Excellent find on that article, Joe.
Definitely wrong as Joe mentioned. Looks like they used teflon on the connector which is wrong and using white teflon to gas pipe fitting is a no no as well. All around homeowner special.
Joe… Good information and thank you for responding so quickly