Originally Posted By: cbuell
This post was automatically imported from our archived forum.
Here is some fun pictures from a 4-plex. This was a 400 amp service with a main disconnect. Next to the main disconnect was this panel with the fuse disconnects with the meters between the fuses and the sub-panels (which were in each unit). Note the fused neutrals. The second pic is a little sub-panel with some over-heating. Lots of issues in the whole place. The panel appears to be original 1927.