Originally Posted By: jpope
This post was automatically imported from our archived forum.
It’s been a while since I’ve seen this condition, so I thought I post a couple pictures.
This was a 1921 build just outside of Los Angeles. If you notice, this system has only two circuits, both ungrounded and both with fused neutrals (which are "no-no's").
There were four - 15 amp - "screw in" fuses (originally) and one was replaced with a 30 amp fuse (wonder why ![icon_wink.gif](upload://ssT9V5t45yjlgXqiFRXL04eXtqw.gif) ). The service cables were both provided with 30 amp cartridge fuses in the main shut-off.
JPI Home Inspection Service
"At JPI, we'll help you look better"