How many code violations can you spot?
Possibly, but it shouldn’t be inside the panel regardless of what it’s for.
I hope you had a type-o. I asked the question with sarcasm. Most doorebel transformer around here are under the home or in a coat closet.
You mean outside right?
No, Bruce, he means shouldn’t
The transformer should be mounted on the outside of the panel or it isn’t grounded.
Picture 4 (of the main lugs is fuzzy) what is your question there?
Yep. Sorry for the typo. . .
725.55 of the NEC normally addressed this situation but the 2008 NEC made significant changes in numbering. Anyone know where it is now?
Picture 4 has a broken plastic isolation ears and neutral conductors (in addition to be jammed under one lug screw) in close proximity to one of the legs.
Sloppy amateur work. I is r eye -litric-gal specialist…
I posted the pics just for humor. The panel was a major mess. I just summed it up by saying there were several issues, and a licensced electrician needed to come out and further inspect, and repair or replace as needed.