At todays inspection, house was built in 1999, and is in the county, not city. The main panel was on the meter pole at the far end of the yard and with no common connection (fence) to the home. 2/0 CU to a 200 Amp panel, with 200 amp main breaker.
In the house was another 200 Amp panel with 3 wire feed, neutrals (grounded) and grounding mixed under the same terminal screw, and it was bonded.
In my tired brain condition tonight this would need (correct me if I’m wrong, please) –
- remove bonding strap
- add grounding bus bar and separate the grounded / grounding conductors
- what about the missing incoming ground?
I would refer to qualified electrician, but I need to know for my own info.