I ran into this on my last “mock” inspection.(yes I’m a newbe" :shock:)
Murray fuse panel. House was built in early 60’s.
- Meter is 200 AMP
- 4/0 Alum SEC (200 AMP)
- 200 AMP rated panel
This is fine and would have said “200 AMP service” The question is the “Plugin Fusible Components” are - 100 AMP (top) and 60 AMP (middle).
There is a 100 AMP “sub-panel” located in another area and there is an add-on breaker for the A/C mounted on top of the main service panel.
All fuses are either 15 or 20 AMP.
My questions – Is this really a 200 AMP service? And should this be updated to a new breaker panel?