I cover the central Florida area. Yesterday I inspected a new construction home with lots of electrical issues. i.e. None of the bathrooms were GFI protected. and ALL the outlets in the master bedroom, half of the outlets in the living room and one exterior outlet were all on the same circuit as the master bedroom lights. So if you switched off the light switch all the power to those outlet is off as well!
So I’m second guessing everything now.
The Home had (2) 150 amps service disconnects located in an exterior panel and two breaker panels in the garage. When I opened them up I found ALL the neutral wires in the panel to the left. Is this OK? Should the neutrals for the circuits in the panel to the right go back to the neutral bus bar in that panel?
Also these panels don’t appear to be properly grounded? (see photos)
Am I correct or off base here? any insight is appreciated.