Originally Posted By: jpope
This post was automatically imported from our archived forum.
Started out bad enough with an FPE and missing knockouts. . .
Then there were these #12 cu connected to 30A breakers. . .
These breakers were actually feeding two 240V outlets in the garage. Follow the blue wires to their connections
How many more defects can you find?
JPI Home Inspection Service
"At JPI, we'll help you look better"