Originally Posted By: psmothers
This post was automatically imported from our archived forum.
Sorry Jeff! Judging by this panel set up I do belive this was suppose to be your inspection!
60 Amp main. All the other equipment panels were double and triple lugged of each other. Multiple double taps on the fuses as well. Half of the system was not grounded.
"Its not a matter of will we rebuilt it is matter of how soon..."
"A hero is no braver than an ordinary man, but he is brave five minutes longer."
- Ralph Waldo Emerson