Correct me if I am wrong, here. :mrgreen:
-House built mid 60’s, service entrance panel
-Split bus panel
-Another set of conductors are attached on lugs beside the SEC lugs, which are then secured further down the panel. At that second securing, it is a double tapped with a smaller wire connecting to the other opposite side.
This makes all breakers hot (not fed from upper breaker) and exceeds the 6-throw rule.
Oh, Stablock panel in hallway. The things we find.!
Thanks for all the input