Originally Posted By: rmoore
This post was automatically imported from our archived forum.
Back on topic…
here's a nice one:
24 year old heater original to the home. Besides the TPR not being in the tank what makes this really screwy is that the discharge line enters the "finished" wall and then re-emerges and terminates back into the garage at the base of the wall. So why bother?
No H/C bonding. Notice the fine use of plumbers tape wrapped around the tank. It,s fastened in one place only with a single screw. Yeah...that'll hold it!
Rest Assured Inspection Services