I did an inspection today and I found an issue that I called out but would like to know what others think.
The 50 amp range breaker had two 10 ga wires at each pole for a total of 4. Besides the obvious double tap, if these wires were soldered together would it be acceptable?
I could not determine where or how the business ends terminated. Any thoughts/comments welcome.
My thanks in advance.