While performing one of the four required mock inspections to become a certified inspector, I noticed the main breaker panel is rated at 150 Amp max, but the shut off is 200 amps. (See attached picture)
Would this be a defect that needs to be addressed?
Where are you seeing the 200 amp rating? The handle-tie on the CB says 150.
Welcome to our forum, Larry!..enjoy participating.
Thank you Robert. After reading your post I went back to the panel (this is in my house) and, looking at it from a different angle I can see the 150. I appreciate that sir
No problem just here to help. And good luck with your certification.
While performing one of the four required mock inspections
Mock inspections NOT 4 point inspection.