Any more pics Brian?
Something else is going on to cause this.
Either way this panel needs some serious rework.
Just some guys finger where a knockout should be.
Typical with loose neutral but would certainly not rule out lighting strike, have have several occasions where lighting only damaged branch circuit conductors