Originally Posted By: jpope
This post was automatically imported from our archived forum.
of Bob’s posts, I rarely have an opportunity to correct
any of his comments
On another note. Can any
breaker be used to energize a panel or does it have to be listed for that purpose? We're all assuming that this panel box is "back-fed" through that 100 amp breaker and hopefully not through the 60 amp breaker.
What about this locking device. . .
Both the 100 amp and 60 amp, 240 volt breakers appear to be locked open. And this whole thing is fed off a 50 amp
JPI Home Inspection Service
"At JPI, we'll help you look better"