Can someone confirm that this is an issue. The second wire appears to be used to feed the subpanel for the pool.
yes double tap not allowed Good catch .
Thanks Roy. And the realtor wants to know how to write it up for repair. Suggestions?
Double tap not allowed Needs to be repaired by an electrician .
The bare conductor on the right is not terminated properly either.
At this point the educator (even if a poor one) in me now wants to make sure the OP understands WHY this is incorrect and what can happen when it is done incorrectly.
This goes a long way in knowing why someone should not do it…rather than that they shall not do it.
So…anyone ( Home Inspector Only) care to give some education as to why this is inappropriate to terminate this way…LOL…and not you Robert…lol