This house was built in 2005. I was surprised to see double tapped neutrals in the main panel that were probably from the original installer because there is nothing in the panel that looks like a home owner modification. The sub panel is fed by a 50 amp breaker. The conductors are 8 awg from the breaker. The pool panel has conduit laying on the ground and what appears to be a neutral landed on the grounding buss.
It is a more sophiscated panel than the old ones with just a timer and a light. I’,m going to call out poor workmanship on the flex conduit, too small of a conductor, double tapped neutrals at the main panel and a neutral landed on the ground buss. Any other thoughts would be appreciated.