Originally Posted By: jtedesco
This post was automatically imported from our archived forum.
This electrical service equipment was already installed, and must have been inspected and met with the approval of the inspector at one time, I am sure, so the subject that goes beyond the original questions is of little value, and the clearances are adequate and look like they met the code in that year whenever.
Joe makes a good point and so does Ryan ...... but it is the .....
Messy wires that are communications, and others that are messy and sloppy, so all I would say is that they should be cleaned up a bit, and if that is not clear then call the telephone, or other utility and ask them to take a look.
I would ask, however, if the original cover on the right was in its up position or missing, and if it was missing I would make that known.
Joe Tedesco, NEC Consultant