Was there supposed to be a picture?
Nope I don’t see anything
Dang phone, you guys are too fast, it hadn’t uploaded it yet.
Looks like some type of fuse holder on the right side- with no fuse and nothing connected to it. Did they remove the fuse and tape the wires together?
No it’s more fun than that.
I see many possibles, pic not large enough. Fuse is bypassed appears to have no wire connected to the green ground screw, a yellow and green wire connected together and the yellow on the low voltage terminal not in use appears they used a blue instead. Possibly to small a run cap for the blower motor
That’s a bat inside the circuit board box inside the blower compartment.
But then I noticed more fur and dropped it down for a better look. Two.:eek:
That’s plain batty! I would have dropped one if those little bastards started flying around.
I have a dry sense of humor just funnin ya;-) but did it make you go back and take a second look your self
Now I’m reading pages of HVAC wiring color codes… Thank you very little!
They were a bit stiff, but I didn’t even think of that while I was dropping that case. :shock:
That is as good as my pic with the mice on the filter. LOL
I would also think that the fuse went and this was temp repair by the HVAC tech. He may have the fuse and forgot to return.:shock::shock:
The fuse looks like it might have been replaced with that panel-mount circuit breaker right behind it.
Your welcome very little
Without going through the thread.
I see a splice where the fuse mount lies empty.!!!
If I remember correctly its a blue 10 or 12 G. wire with electrical tape.
Like to share the link??? We all like codes.
Thanks in advance.
He should have read the thread, eh?