Originally Posted By: Greg Fretwell
This post was automatically imported from our archived forum.
We had this basic discussion when Joe had a wad in his panties about a “damaged insulation” beef and we talked about stripping the wire. I defy someone to find a NEC violation with this if it is more than 1/4" from any other energized conductor or the “can” if this isn’t the service disconnect enclosure.
It is sloppy and may be a workmanship problem but it may not be a violation.
If I am inspecting this job I would shame the installer into making this look a little better. In your job I am not sure how you score it.
Babies are not going to die but it sure ain’t pretty.