The home I inspected today had an updated rectangular meter installed.
The main panel was 100 amps.
It appeared to me that the wires from the weather head to the top of the meter were not updated. (See photo)
I also thought the connection to the main service wires was inadequate.
Also in the main panel it appeared to have 14 gauge romex to 20 amp breakers. The romex ran along the basement but there where no markings on the sheathing. (See photos)
Am I wrong in saying that the service may only be 60 amps because of the service wires at the weather head.
I called out a sparky for the weather head & undersized wires.
Do you see anything else that I may have missed?